HSM101812U18FG(0.125 gpf/0.5 Lpf) FLUSH GENIE® SIDE MOUNT TIMER/SENSORHEU HALF STALL URINAL FLUSH VALVE SYSTEM
DESCRIPTIONBattery Powered, Sensor/Programmable Timer OperatedFLUSH GENIE® Side Mount Complete Ultra HEU Systemwith Exposed Urinal Flushometer and Vitreous China Fixture.
FLUSH CYCLEModel HSM101812U18FG (0.125 gpf/0.5 Lpf) High Efficiency
FLUSHOMETER SPECIFICATION (HSM-801FG-CU-18)- Patented Gear Motor Drive- Built-in Sensor Mode and Timer Mode for Ultimate Functionality- Programmable Settings on Timer Mode Allow Flushing Once Every 30 minutes, 1, 2, or 3 Hours- Electronic Push Button- Front (Sensor Mode Only)- Mechanical Override- Side (Using Manual Flush Key)- Vandal and Water Resistant Design- Chrome Plated Metal Housing- Quiet Operation- Operates on (4) “C” Alkaline Batteries (Included)- Battery Life - 3+ Years- “Low Battery” Blinking LED Indicator - Easy Battery Replacement-No Water Shut Off Necessary- Adjustable Sensor Distance (Sensor Mode Only)- Optional (3) Second Flush Delay (Sensor Mode Only)- Optional 24-Hour Flush (Sensor Mode Only)- Uses Proprietary Silicone Diaphragm with Filtered Bypass- 3/4” I.P.S. Angle Stop- Adjustable Tailpiece- High Back Pressure Vacuum Breaker with Single Piece Hex Coupling Nut- Spud Coupling and Flange for 3/4” Top Spud - Sweat Solder Kit and Wall Flange with Set Screw- High Efficiency For Water Conservation
PLUMBING SYSTEM REQUIREMENTS- Minimum Flowing Pressure: 25 PSI- Maximum Static Pressure: 80 PSI- Minimum Flow Rate: 25 GPM
The FLUSH GENIE® is a fully programmable automatic flush device forurinals and toilets. The smart design allows the device to be switchedbetween sensor activated mode and timer controlled mode. When inSENSOR activated mode, the unit sends out an infrared beam that sensesa user on a urinal or toilet. Once the user walks away from the fixture theunit triggers the fixture to flush automatically. The unit includes anelectronic push button to allow for a courtesy flush option. When in TIMER controlled mode, the unit converts most urinals into waterefficient fixtures by controlling the amount of daily flushes. The flushintervals can be programmed to flush once every 30 minutes, 1, 2, or 3 Hours.The unit will go to SLEEP if a user is NOT detected within 135 minutes since thelast use to prevent flush activation while the facility is closed. A mechanical manual flush override using the provided MANUAL FLUSH KEY will allow the custodial staff (not the user) to flush the unit manually at any time. (Note: electronic push button is deactivated in TIMER mode).